Introductory overview Almost all coal, nuclear, geothermal, solar thermal electric, and waste incineration plants, as well as many natural gas power plants are thermal. Natural gas is frequently combusted in gas turbines as well as boilers. The waste heat from a gas turbine can be used to raise steam, in a combined cycle plant that improves overall efficiency. Power plants burning coal, oil, or natural gas are often referred to collectively as fossil-fuel power plants. Some biomass-fueled thermal power plants have appeared also.
Non-nuclear thermal power plants, particularly fossil-fueled plants, which do not use co-generation are sometimes referred to as conventional power plants. Commercial electric utility power stations are most usually constructed on a very large scale and designed for continuous operation. Electric power plants typically use three-phase or individual-phase electrical generators to produce alternating current (AC) electric power at a frequency of 50 Hz or 60 Hz (hertz, which is an AC sine wave per second) depending on its location in the world.
Other large companies or institutions may have their own usually smaller power plants to supply heating or electricity to their facilities, especially if heat or steam is created anyway for other purposes. Shipboard steam-driven power plants have been used in various large ships in the past, but these days are used most often in large naval ships. Such shipboard power plants are general lower power capacity than full-size electric company plants, but otherwise have many similarities except that typically the main steam turbines mechanically turn the propulsion propellers, either through reduction gears or directly by the same shaft.The steam power plants in such ships also provide steam to separate smaller turbines driving electric generators to supply electricity in the ship. Shipboard steam power plants can be either conventional or nuclear; shipboard nuclear plants are with very few exceptions only in naval vessels. There have been perhaps about a dozen turbo-electric ships in which a steam-driven turbine drives an electric generator which powers an electric motor for propulsion.
In some industrial, large institutional facilities, or other populated areas, there are combined heat and power (CH&P) plants, often called co-generation lants, which produce both power and heat for facility or district heating or industrial applications.AC electrical power can be stepped up to very high voltages for long distance transmission with minimal loss of power. Steam and hot water lose energy when piped over substantial distance, so carrying heat energy by steam or hot water is often only worthwhile within a local area or facility, such as steam distribution for a ship or industrial facility or hot water distribution in a local municipality. edit] HistoryReciprocating steam engines have been used for mechanical power sources since the 18th Century, with notable improvements being made by James Watt. The very first commercial central electrical generating stations in the Pearl Street Station, New York and the Holborn Viaduct power station, London, in 1882, also used reciprocating steam engines.
The development of the steam turbine allowed larger and more efficient central generating stations to be built.By 1892 it was considered as an alternative to reciprocating engines  Turbines offered higher speeds, more compact machinery, and stable speed regulation allowing for parallel synchronous operation of generators on a common bus. Turbines entirely replaced reciprocating engines in large central stations after about 1905. The largest reciprocating engine-generator sets ever built were completed in 1901 for the Manhattan Elevated Railway. Each of seventeen units weighed about 500 tons and was rated 6000 kilowatts; a contemporary turbine-set of similar rating would have weighed about 20% as much.EfficiencyThe energy efficiency of a conventional thermal power station, considered as salable energy (in MW) produced at the plant busbars as a percent of the heating value of the fuel consumed, is typically 33% to 48% efficient. This efficiency is limited as all heat engines are governed by the laws of thermodynamics (See: Carnot cycle). The rest of the energy must leave the plant in the form of heat.
This waste heat can go through a condenser and be disposed of with cooling water or in cooling towers. If the waste heat is instead utilized for district heating, it is called co-generation.An important class of thermal power station are associated with desalination facilities; these are typically found in desert countries with large supplies of natural gas and in these plants, freshwater production and electricity are equally important co-products.
A Rankine cycle with a two-stage steam turbine and a single feed water heater. Since the efficiency of the plant is fundamentally limited by the ratio of the absolute temperatures of the steam at turbine input and output, efficiency improvements require use of higher temperature, and therefore higher pressure, steam.Historically, other working fluids such as mercury have been experimentally used in a mercury vapor turbine power plant, since these can attain higher temperatures than water at lower working pressures.
However, the obvious hazards of toxicity, and poor heat transfer properties, have ruled out mercury as a working fluid. Above the critical point for water of 705 °F (374 °C) and 3212 psi (22. 06 MPa), there is no phase transition from water to steam, but only a gradual decrease in density. Boiling does not occur and it is not possible to remove impurities via steam separation.In this case a super critical steam plant is required to utilize the increased thermodynamic efficiency by operating at higher temperatures. These plants, also called once-through plants because boiler water does not circulate multiple times, require additional water purification steps to ensure that any impurities picked up during the cycle will be removed. This purification takes the form of high pressure ion exchange units called condensate polishers between the steam condenser and the feed water heaters.
Sub-critical fossil fuel power plants can achieve 36–40% efficiency.Super critical designs have efficiencies in the low to mid 40% range, with new “ultra critical” designs using pressures of 4400 psi (30. 3 MPa) and dual stage reheat reaching about 48% efficiency. Current nuclear power plants operate below the temperatures and pressures that coal-fired plants do. This limits their thermodynamic efficiency to on the order of 30–32%.
Some advanced reactor designs being studied, such as the Very high temperature reactor, Advanced gas-cooled reactor and Super critical water reactor, would operate at temperatures and pressures similar to current coal plants, producing comparable thermodynamic efficiency.